Anatomy of a Conductor, Part 4: Branch Circuit Basics
This issue continues our series on the anatomy of a conductor. It is the first that focuses on the heart of the power distribution system: the branch circuit. And this article also returns to our analysis of sizing the conductor. In this case, the branch circuit conductor.
NEC Article 100 "Definitions" defines branch circuit (BC) as "The circuit conductor between the final overcurrent protection device (OCPD) protecting said circuit and the outlet(s)."
The same article also defines outlet as "A point on the wiring system at which current is taken to supply utilization equipment."
Combining the base current value previously calculated in Part 3 of this series, with the two definitions above, the complete design of the branch circuit requires the following:
A branch circuit is rated according to the trip setting of the OCPD that protects the circuit conductors (NEC Section 210.3), with some exceptions that will be discussed at length in future articles.
NEC Article 100 also tells us that there are four (4) types of branch circuits:
The NEC distinguishes and defines these four (4) types of branch circuits because it limits the OCPD rating of any branch circuit with more than one outlet to 15, 20, 30, 40 and 50 Amps (See NEC 210.3). This requirement also applies to branch circuits other than individual branch circuits. As an example, if you have a 60 Amp or 25 Amp branch circuit with two (2) or more outlets, then this requirement is not applicable.
NEC Article 100 also includes in the definitions of receptacle (RCPT), that a duplex RCPT is considered to be two (2) outlets. Any branch circuit for a duplex RCPT must also conform to the requirements of NEC 210.3, and any outlet rated above 50 Amps should be connected on an individual branch circuit.
As a field note: it is an observation that an indoor air handling unit (AHU) with heating strip and the associated outdoor condensing unit (CU) are sometimes observed to be designed on a single one (1) 60 Amp circuit. This is a direct violation of NEC 210.3.
The discussion of the complex requirement of the conductor will continue in future newsletters.
Save Time / Save Money
PowerCalc automates the electrical design process.
It is well established that automation is the driver in our techcentric society and business world.
Automation drives productivity across all businesses large or small. Changes, even small ones, over time snowball into massive gains in productivity.
It includes: automation of processes with databases, standards, and updated procedures resulting in fewer errors, fewer building department comments and fewer issues with finished designs. And, just less time spent on design and repetitive calculations.
To illustrate this point, we’ve put together the chart shown that focuses on design time. It shows how PowerCalc streamlines the design process to save days of engineering man hours. Save Time/Save Money.
Let me know what you think…sign up for our blog.