August 15, 2017

**CORRECTION RE-ISSUE: Anatomy of a Conductor Part 3: Voltage Levels and Base Current Value**

This issue continues discussion on the anatomy of a conductor. It focuses on voltage levels and base current value.

Base Current Value

In Part 1, we discussed the different types of conductors in relation to their location in the building's power distribution system and the service provided. Anatomy of a Conductor, Part 1 The types are service conductors, service entrance conductors, feeder conductors, branch circuit conductors, ground electrode conductor and neutral conductor. The factors to consider in meeting the NEC's detailed but confusing requirements were also listed. Then in Part 2, we discussed sizing the conductor. Anatomy of a Conductor Part 2

Back to factors, those for consideration by the electrical professional can be organized into three categories: (1) *Primary Factors*, (2) *Secondary Factors* and (3) *Ancillary Factors*.

*Primary Factors* are those used to determine load as "seen" by the conductor: (1) system voltage, (2) system phase, (3) equipment # of poles, (4) equipment utilization voltage and (5) total electrical loads.

*Secondary Factors* are those that impact the size and type of conductor as referenced in the NEC. These include: (1) temperature limitations, (2) temperature correction factor, (3) adjustment factor, (4) equipment grounding conductor, (5) load type (receptacle, lighting, motor and welding equipment), (6) conductor insulation (TW, THW, THHN and others), (7) ground electrode conductor and (8) material (CU or AL).

Last, there are the *Ancillary Factor*s that support the *Secondary Factors*. These are design driven and considered in relation to installation. They include: (1) voltage drop, (2) conductors in parallel, (3) tap rule, (4) current carrying conductor, (5) demand load calculation and (6) amperage interrupting capacity (AIC).

The outcome of applying the *Primary Factors* is the base current value in AMPS. The designer based on design requirements and location, then applies the *Secondary Factors* to obtain conductor size and the associated overcurrent protection device (OCPD). Once these 2 basic values are determined, then the designer finally applies the* Ancillary Factors* to complete the design and specify the correct wire size and insulation rating.

Voltage Levels

The *Primary Factors* are applied as part of the following basic engineering equation for power to determine the base current value (l).

P = l x V x √3 for a 3 Φ distribution system

P + l x V for a single Φ - 1 pole and single Φ - 2 pole distribution system

Where P stands for Power (VA); V stands for Volt (V); l stands for Current (A)

Any electrical circuit, in its simplest form, consists of two wires which carry electrical current at a voltage level (electrical potential). The motion of the free electrons (charges) in a given electrical potential in a solid conductor constitutes an electric current (l). Said electric current (l) travels at the speed of light (186,000 miles/second). The unit of electric current is Ampere (Amps). One Ampere of current = 6.251 x 10 to the power of 18 electrons pass given cross section in 1 sec.

The higher the voltage, the higher the current flow for a given resistance. The flow of current (l) in an electric circuit is impeded by the resistance (R) [R = V / l] and produces heat (wasted energy). This wasted energy can be calculated by the following equation: P = l² R.

It is because of this equation, one should properly size the conductor to minimize wasted energy.

Distribution systems in a building are classified according to the voltage level used to transfer the power needed to operate its equipment. The most common distribution system voltage levels that are widely used in the United States are:

480Y / 277 V 3 Φ; 208Y / 120 V - 3 Φ; 230 V closed Δ, 3 Φ; 230 V open Δ; 230 V - 2 poles, 1 Φ; 120 V - 1 pole

In summary, the voltage, the phase, equipment # of poles, equipment utilization voltage and total electrical loads determine the base current value.

This discussion about the complex requirements of the conductor will continue in future newsletters.

Save Time / Save Money

*PowerCalc *automates the electrical design process.

It is well established that automation is the driver in our techcentric society and business world.

Automation drives productivity across all businesseslarge or small. Changes, even small ones, over timesnowball into massive gains in productivity.

It includes: automation of processes with databases,standards, and updated procedures resulting in fewererrors, fewer building department comments and fewer issues with finished designs. And, just less time spent on design and repetitive calculations.

To illustrate this point, we’ve put together the chartshown that focuses on design time. It shows how*PowerCalc *streamlines the design process to **save ****days of engineering man hours**. Save Time/Save Money.

Let me know what you think…sign up for our blog.

488 N. Federal Hwy, Boynton Beach, Florida 33435

(561) 278-9969

Inbound Performance Template by SmartBug Media. Copyright 2021.

All Rights Reserved